Water Based Fire Extinguishing Systems
Calculations. For any fire modeling generated results,
Installation of waterflow switches and
submit a copy of the input data and all pertinent program
material and assumptions required to understand the
Sprinkler floor control valves, sectional valves,
output and the analysis. A narrative of the input and
and inspector text assembly.
results shall be part of the calculations.
1. Final occupant load and egress calculations.
Non-Water Based Fire Extinguisher Systems
2. Final fire protection water supply calculations.
Special fire extinguishing systems
Includes water supply flow testing data.
(e.g., wet chemical, etc.).
3. Final fire pump calculations where applicable.
Fire Alarm System
4. Final smoke control calculations where applicable
Fire alarm riser.
(e.g., atrium, etc.).
Typical firefighter telephone station.
Typical firefighter telephone jack.
Electrical closets for fire alarm system panels.
6. Fire modeling.
Fire alarm telephone panel (includes voice paging
7. Final calculations contained in The SFPE Handbook
microphone and firefighter telephone system).
of Fire Protection Engineering for calculating sound
Visual indicating device control and power detail,
typical for floors (state location).
and location of fire alarm system audible notification
Amplifier rack (state location).
Outdoor fire alarm speaker.
Wall mounted cone fire alarm speaker.
Typical terminal cabinet.
Lay in ceiling mounted fire alarm speaker.
Lay in ceiling mounted fire alarm combination
Wall mounted strobe device.
Typical manual fire alarm box installation.
Fire alarm system input/output matrix.
Graphic annunciator panel.
Installation of the graphic annunciator.
Fire command center showing the locations of
each panel to be installed.
346 F A C I L I T I E S S T A N D A R D S
A.4 Alteration Projects Construction Documents
Revised March 2005 PBS-P100