1. Project title sheet, drawing index.
specialist qualification requirements, Sections 00120 and
009, cross referenced in material specifications.
2. Demolition plans.
3. Floor plans.
historic materials, including:
Show planning grids and raised access floor grid,
Specialized materials and procedures for repair
and restoration of historic materials.
4. Reflected ceiling plans.
Procedures for protecting historic materials in
Show ceiling grid and location of all elements to
areas being altered.
be placed in the ceiling.
Sample review requirements of repair and
5. Building sections.
Sample submittal requirements for replacement
Vertical zoning for electrical and mechanical
materials and new installations in preservation
utilities must be indicated on sections.
6. Roof plans.
Roof plans must show slopes, low points, drains
and scuppers, equipment, equipment supports,
roof accessories and specialty items, if applicable.
7. Exterior elevations.
1. Demolition plans (when applicable).
8. Wall sections.
2. Full set of structural construction drawings.
9. Interior elevations.
Drawings must be fully dimensioned, noted and
detailed for accurate bidding and construction.
Load criteria for all floor live loads, roof live load,
Schedules.Diagrams illustrating proper clearance for
roof snow load, wind load, earthquake design
servicing and replacement of equipment.
data, and special loads must be shown on
drawings. Live load reduction of the uniformly
distributed floor live loads, if used in the design,
1. Room finish, ceiling types, floor finish, color and
shall be indicated.
door schedules can be incorporated into either the
Basic wind speed (3-second gust), miles per hour
specifications or drawings.
(km/hr), Wind importance factor, I, and building
2. Call for thermographic scans of building envelope to
category, Wind exposure, the applicable internal
identify sources of heat transfer.
pressure coefficient must be indicated.
3. Call for assembly of mock-ups for spaces such as
Seismic design criteria, such as Seismic use group,
courtrooms and sample office space fitouts.
Spectral response coefficients SDS and SD1, Site
class, Basic seismic-force-resisting system, Design
4. Provide lighting fixture type schedule.
base shear, and analytical procedure must be
324 F A C I L I T I E S S T A N D A R D S
Revised March 2005 PBS-P100